Fields with asterisks* are required. Your friend will receive an email that contains a reference to this page. Please send this email only to people you know who would be interested in this information.
Size: 10” x 8” (254 mm x 203 mm) Flanged. Casing: Ductile Iron 65‐45‐12. Maximum Casing Pressure 265 psi (1827 kPa).* Maximum Operating Pressure 250 psi (1723 kPa) at Temperatures up to 100F (37C) Based on System Component Limitations.* Enclosed Type, Two Vane Impeller: Ductile Iron 65‐45‐12. Handles 3” (76,2 mm) Diameter Spherical Solids. Suction Head: Gray Iron 30. Suction Spool: Gray Iron 30. Impeller Shaft: Alloy Steel 4150M. Externally Adjustable, Replaceable Wear Ring: Ductile Iron 65‐45‐12. Pedestal: Gray Iron 30. Seal Plate: Gray Iron 30. Shaft Sleeve: Stainless Steel 303/304. Priming Chamber: Gray Iron 30 Housing w/Stainless Steel Float and Linkage. Discharge Check Valve: Ductile Iron Housing w/Buna‐N Flapper. Radial Bearing: Open Roller. Thrust Bearing: Open Double Ball. Bearing and Seal Cavity Lubrication: SAE 30 Non‐Detergent Oil. Gaskets: Red Rubber and Buna‐N. O‐Rings: Buna‐N. Hardware: Standard Plated Steel. Bearing and Seal Cavity Oil Level Sight Gauges. * Consult Factory for Applications Exceeding Maximum Pressure and/or Temperature Indicated.